The Watt's New articles serve to keep you abreast of what has been going on around the C.A.R.L.A. Network. Feel free to browse our archive of past Watt's New articles as well.
On this page:
CARLA 32 back on commercial power
Last updated on March 17, 2016 by The C.A.R.L.A. Team | This article is Archived | Permalink
CARLA 32, Pacifica; Commercial power has been restored and is back on-line. Actually, the power
was restored a couple of days ago but the power supply was still OOS and reporting on battery
The San Mateo Coast RRFT responded to the site today and put in a temporary p.s. in place of
the damaged one. Luckily, the new battery charger (which was also replaced after the last power
outage) was still running and keeping the batteries charged. Otherwise, we would have probably
lost battery reserves within another day or so.
We are still actively working on finishing the design and procuring a new solar system for the
site which we hope to have installed sometime in the next few weeks.
The CARLA Team